additional info American Conduit rigid aluminum electrical metallic tubing (EMT) uses a 6005 alloy, 98.5% pure aluminum.
http://gdassociates.xyz/portfolio/page/3/ Specification Compliance:
- Underwriters’ Laboratories UL 797
- ANSI C80 3
hombre quiere conocer mujer American Conduit rigid aluminum conduit is shipped with color coded bundle tape to simplify size selection.
25 year old female dating 18 year old male For more information about composition, sizes, and weight, please contact us at 1-800-334-6825.
citas hombres lobo Recommended Installation Practices:
see it here Cutting: Cut the EMT square using a hacksaw or band saw. Do not use roll-type, tubing cutters. Take special care not to flare the ends when reaming the inside of EMT.
100 free shemale dating sites Bending: Conventional EMT bending equipment (hand, ratchet, power) may be used for Aluminum EMT.
Recommended Site Fittings: Zinc die-cast fittings are recommended, but standard EMT fittings are satisfactory for most installations.
additional reading Fishing and Wire Pulling: Polyethylene fish tapes and polypropylene rope are recommended. Use of flat steel tapes should be avoided.
http://www.hawkerucc.org/monaxinja/3565 Soil or Concrete Installation: Underwriters’ Laboratories Electrical Construction Equipment Directory (UL Green Book) states that aluminum conduit used in concrete or in contact with soil requires supplemental corrosion protection. Examples are paints and tape wraps approved for the purpose, or PVC coated aluminum conduit.